<p>10W Single Output Industrial DIN Rail Power Supply, 12V, 85~264VAC In, 12VDC/10W Out , - 20 ℃ ~ 70 ℃, 3 Year Warranty, Supports: AW-IHS-0200,AW-IHS-0201,AW-IHS-0203</p>
<h3>Technical Specification</h3>
<h3>OUTPUT</h3>
<p>DC VOLTAGE: 12V<br />
RATED CURRENT: 0.84A<br />
CURRENT RANGE :0 ~ 0.84A<br />
RATED POWER: 10W<br />
RIPPLE &amp; NOISE (max.) Note.2: 120mVp-p<br />
VOLTAGE TOLERANCE Note.3: ±3.0%<br />
LINE REGULATION: ±1.0%<br />
LOAD REGULATION: ±3.0%<br />
SETUP, RISE TIME Note.5: 500ms, 30ms/230VAC 1000ms, 30ms/115VAC at full load<br />
HOLD UP TIME (Typ.): 120ms/230VAC 25ms/115VAC at full load</p>
<h3>INPUT</h3>
<p>VOLTAGE RANGE: 85 ~ 264VAC 120 ~ 370VDC<br />
FREQUENCY RANGE: 47 ~ 63Hz<br />
EFFICIENCY (Typ.): 81%<br />
AC CURRENT (Typ.): 0.33A/115VAC 0.21A/230VAC<br />
INRUSH CURRENT (Typ.): COLD START 35A/115VAC 70A/230VAC<br />
LEAKAGE CURRENT: &lt;1mA / 240VAC</p>
<h3>PROTECTION</h3>
<p>OVERLOAD:<br />
Above 105% rated output power<br />
Protection type : Hiccup mode, recovers automatically after fault condition is removed<br />
OVER VOLTAGE:<br />
13.8 ~ 16.2V<br />
Protection type : Shut down o/p voltage, re-power on to recover</p>
<h3>FUNCTION</h3>
<p>DC OK ACTIVE SIGNAL (max.): 9 ~ 13.5V / 40mA</p>
<h3>ENVIRONMENT</h3>
<p>WORKING TEMP.: -20 ~ +70℃ (Refer to "Derating Curve")<br />
WORKING HUMIDITY: 20 ~ 90% RH non-condensing<br />
STORAGE TEMP., HUMIDITY: -40 ~ +85℃, 10 ~ 95% RH<br />
TEMP. COEFFICIENT: ±0.03%/℃ (0 ~ 50℃)<br />
VIBRATION: Component:10 ~ 500Hz, 2G 10min./1cycle, 60min. each along X, Y, Z axes; Mounting: Compliance to IEC60068-2-6</p>
<h3>SAFETY &amp; EMC (Note 4)</h3>
<p>SAFETY STANDARDS: UL508, TUV EN60950-1 approved<br />
WITHSTAND VOLTAGE: I/P-O/P:3KVAC I/P-FG:2KVAC O/P-FG:0.5KVAC<br />
ISOLATION RESISTANCE: I/P-O/P, I/P-FG, O/P-FG:100M Ohms / 500VDC / 25℃/ 70% RH<br />
EMC EMISSION: Compliance to EN55011, EN55022 (CISPR22), EN61204-3 Class B, EN61000-3-2,-3<br />
EMC IMMUNITY: Compliance to EN61000-4-2, 3, 4, 5, 6, 8, 11, EN55024,EN61000-6-1,EN61204-3, light industry level, criteria A</p>
<h3>OTHERS</h3>
<p>MTBF: 584K hrs min. MIL-HDBK-217F (25℃)<br />
DIMENSION: 22.5*90*100mm (W*H*D)<br />
PACKING: 0.17Kg; 72pcs/13.2Kg/0.91CUFT</p>
<h3>NOTE</h3>
<p>1. All parameters NOT Specially mentioned are measured at 230VAC input, rated load and 25 °C of ambient temperature.<br />
2. Ripple &amp; noise are measured at 20MHz of bandwidth by using a 12” twisted pair-wire terminated with a 0.1uf &amp; 47uf parallel capacitor<br />
3. Tolerance: includes set up tolerance, line regulation and load regulation.<br />
4. The power supply is considered a component which will be installed into a final equipment. The final equipment must be re-confirmed that it still meets<br />
EMC directives. For guidance on how to perform these EMC tests, please refer to “EMI” testing of component power supplies.”<br />
5. Length of set up time is measured at cold first start. Turning ON/OFF power supply may lead to increase to the set up time.</p>
