<p>HLG-240H-54: 240W Single Output Switching Power Supply, 54V, 90~305VAC In ,54VDC/240W Out ,IP67, - 40 ℃ ~ 70 ℃, 3 Year Warranty, Supports: AW-IHU-0600</p>
<p>&nbsp;</p>
<p>Technical Specifications</p>
<p>MODEL: HLG-240H-54</p>
<h3>OUTPUT</h3>
<p>DC VOLTAGE: 54V<br />
CONSTANT CURRENT REGION Note.4: 27 ~ 54V<br />
RATED CURRENT: 4.45A<br />
RATED POWER: 240.3W<br />
RIPPLE &amp; NOISE (max.) Note.2: 350mVp-p<br />
VOLTAGE ADJ. RANGE Note.6:  50 ~ 57V<br />
CURRENT ADJ. RANGE:<br />
Can be adjusted by internal potentiometerA type and C type only<br />
2.23 ~ 4.45A<br />
VOLTAGE TOLERANCE Note.3: ±1.0%<br />
LINE REGULATION: ±0.5%<br />
LOAD REGULATION Note.8: ±0.5%<br />
SETUP, RISE TIME Note.9: 1000ms,80ms/115VAC 500ms,80ms/230VAC at full load<br />
HOLD UP TIME (Typ.): 15ms at full load 230VAC /115VAC</p>
<h3>INPUT</h3>
<p>VOLTAGE RANGE Note.5: 90 ~ 305VAC 127 ~ 431VDC<br />
FREQUENCY RANGE: 47 ~ 63Hz<br />
POWER FACTOR (Typ.): PF&gt;0.98/115VAC, PF&gt;0.95/230VAC at full load (Please refer to "Power Factor Characteristic" curve)<br />
TOTALHARMONICDISTORTION: THD&lt; 20% when output loading≧50% at 115VAC/230VAC input and output loading≧75% at 277VAC input<br />
EFFICIENCY (Typ.): 92.5% 93.5%<br />
AC CURRENT (Typ.): 4A / 115VAC 2A / 230VAC 1.2A / 277VAC<br />
INRUSH CURRENT (Typ.): COLD START 75A(twidth=570μs measured at 50% Ipeak) at 230VAC<br />
MAX. No. of PSUs on 16A<br />
CIRCUIT BREAKER 2 units (circuit breaker of type B) / 4 units (circuit breaker of type C) at 230VAC<br />
LEAKAGE CURRENT: &lt;0.75mA / 277VAC</p>
<h3>PROTECTION</h3>
<p>OVER CURRENT Note.4:<br />
95 ~ 108%<br />
Protection type : Constant current limiting, recovers automatically after fault condition is removed<br />
SHORT CIRCUIT Hiccup mode, recovers automatically after fault condition is removed<br />
27 ~ 34V 60 ~ 67V<br />
OVER VOLTAGE:<br />
Protection type : Shut down and latch off o/p voltage, re-power on to recover<br />
OVER TEMPERATURE Shut down o/p voltage, recovers automatically after temperature goes down</p>
<h3>ENVIRONMENT</h3>
<p>WORKING TEMP.: -40 ~ +70℃ (Refer to "Derating Curve")<br />
WORKING HUMIDITY: 20 ~ 95% RH non-condensing<br />
STORAGE TEMP., HUMIDITY: -40 ~ +80℃, 10 ~ 95% RH<br />
TEMP. COEFFICIENT: ±0.03%/℃ (0 ~ 50℃)<br />
VIBRATION: 10 ~ 500Hz, 5G 12min./1cycle, period for 72min. each along X, Y, Z axes</p>
<h3>SAFETY &amp; EMC</h3>
<p>SAFETY STANDARDS Note.7:<br />
UL1012, CAN/CSA-C22.2 No. 107.1-01, UL8750, CSA C22.2 No. 250.0-08, TUV EN61347-1, EN61347-2-13 independent<br />
(except for HLG-240H C type), UL60950-1, UL8750, TUV EN60950-1, IP65 or IP67, J61347-1, J61347-2-13 approved<br />
WITHSTAND VOLTAGE: I/P-O/P:3.75KVAC I/P-FG:2KVAC O/P-FG:1.5KVAC<br />
ISOLATION RESISTANCE: I/P-O/P, I/P-FG, O/P-FG:100M Ohms / 500VDC / 25℃/ 70% RH<br />
EMC EMISSION: Compliance to EN55015, EN55022 (CISPR22) Class B, EN61000-3-2 Class C (≧50% load) ; EN61000-3-3<br />
EMC IMMUNITY: Compliance to EN61000-4-2,3,4,5,6,8,11, EN61547, EN55024, light industry level (surge 4KV), criteria B</p>
<h3>OTHERS</h3>
<p>MTBF: 207.9K hrs min. MIL-HDBK-217F (25℃)<br />
DIMENSION: 244.2*68*38.8mm (L*W*H)(HLG-240H-Blank/A/B) 251*68*38.8mm (L*W*H)(HLG-240H-C)<br />
PACKING: 1.3Kg; 12pcs/16.6Kg/0.84CUFT(HLG-240-Blank/A/B) 1.23Kg; 12pcs/15.8Kg/1.16CUFT(HLG-240-C)</p>
<h3></h3>
<p>&nbsp;</p>
